How Can Preventative Maintenance Of Filters Ensure The Highest Quality UPW At Lowest Cost Of Ownership?
By Gerd Heser & Jochen Ruth
Filters Ion-exchange Monitoring Particles Troubleshooting
In today’s advanced semiconductor fabs, ultrafiltration (UF) is used as the final filter step in ultrapure water (UPW*) supply plants. It eliminates nanoscale particles, macromolecules and pyrogens. UF has proven to be a highly reliable technology requiring low maintenance and enabling long change-out cycles.
UF even withstands episodic increase of particle numbers in the feed (e.g., caused by conditioning of ion-exchange resins) without negative effects for water quality and service lifetime. Such a particle challenge typically involves high concentrations of ~10-nanometer (nm) particles. On the other hand, current on-line particle counters approach their lower detection limit at about 10 nm. Large numbers of particles nearby and below this limit remain undetected. Hence, the integrity of a UF membrane is essential to keep these small particles under control; it can hardly be evaluated by comparing particle counts upstream and downstream. Therefore, better test methods are needed to identify membrane damages, and to decide on service life and replacement of UF membranes.
Log in or Subscribe to Access the Full Article
To read or download full-length articles you need a subscription to Ultrapure. Please log in or subscribe below.
Password ResetIf you have forgotten your password, or have not yet set one, you can reset it by email.